Service hoist cage was chaired at shaft collar, when hoist man attempted to move cage upward, DC breaker tripped and would not reset. Initial evaluation indicated hoist would be down more than 30 min. UG employees evacuated safely. SCR failure, components were 30+ years old. Common SCR's from an out of service unit were used to restore function.
U.S. Mine Safety and Health Administration